Some electric car charging station installations require a power management system to ensure power consumption is constrained to the service panel capacity. The “service panel” being the grey box containing circuit breakers for each circuit, and the master circuit breaker for the panel. Service panel capacity is what constrains the total number of charging stations at a given facility, and when charging station requirements grow larger than service panel capacity the host site faces the expensive prospect of upgrading their service panel.
That is – Typical EVSE’s (charging station) today are designed to connect with a 40 amp circuit, providing 32 amps to the car. At 208 volts (typical for commercial power) that is slightly over 6 kilowatts, and at 240 volts that’s 6.6 kilowatts. In any case, a bank of 10 EVSE’s then requires 400 amps electrical service capacity. (10x 40 amps = 400 amps)
But we’re facing a future of ever more electric cars being sold, and a constantly growing need for electric car charging stations. That means host sites will like charging station products with which they can increase the number of charging stations, without increasing service panel capacity.
What if there were a way to have 20 or 30 EVSE’s on 400 amps of service panel capacity?
A few companies are working on systems to do that. What I’m about to describe is my thoughts on a simple way to implement such a system.
Let’s start with this image. You’ll see it has two connections to the electricity grid, one for the building power and the other for the local charging station network. As I said in the immediately previous post – it’s useful to separate these for accounting purposes, such as achieving Net Zero Energy goals. Let’s not get too hung up on that, and look at some other aspects of this system idea.
Instead of giving each charging station a simple connection to the service panel, with no coordination between the stations, I’ve drawn a box labeled “Local Charging Network Controller”. Say what?
What we’re designing is a “charging station network” for a local site. Let’s see what we can do without having to involve another company to remotely manage the charging facilities.
To that end, let’s design a small scale computer that would be tightly coupled to the service panel. This computer needs connection to and control over every charging station. It doesn’t have to be a big expensive computer server — today’s computer technology has managed to produce miniscule computers with the computing/transaction power of earlier behemoths.
Here’s details on what’s going on between the car and the Local Charging Network Controller. (Apologies for using a gas pump icon to represent the charging station)
Let’s take the top two points together
- Watches the power consumption of all charging stations in the local network
- Adjusts power consumption of each station up/down to keep the system within power constraints
The only way to share a 400 amp circuit with 30 charging stations is by adjusting the power consumption at each station to keep the whole system within 400 amps. (The numbers have to be adjusted depending on local conditions) Otherwise the host site can only support 10 charging stations off the 400 amp capacity, and the expansion to 30 stations requires 1200 amps of capacity.
Those of you complaining about the lack of charging stations at each site – this is the cause. Service panel capacity constraints limit the number of charging stations at a site.
This design is meant to allow increasing the number of charging stations, without triggering the need for more service panel capacity.
The strategy is adjusting charging station power consumption on each circuit. Staying with our 400 amp service panel, it can support 10 charging stations running at a full 32 amp rate. As soon as 11 cars or more are charging, the network control computer has to start managing power load. At 11 charging stations the safe rate per station is 29 amps, at 12 stations the safe rate is 26 amps per station, at 23 stations the safe rate per station drops to 14 amps, and so on.
The power rate is adjusted between the car and the charging station using the J1772 pilot signal. Electric cars are supposed to respond to this signal and adjust the charging rate to match.
The normal purpose of the pilot signal is so a car with a powerful on-board charger can use a lower capacity charging station without causing a fire. Otherwise the cars with an on-board 10 kiloWatt charger would overdrive a 3.3 kiloWatt charging station, heating up the wires, and if the circuit breaker doesn’t trip causing a fire.
The local charging network controller has to send a command signal to the charging station so it can in turn adjust the pilot signal so the car ramps down its charging rate. The controller must do this based on the number of connected cars, sharing out power to keep it within the service panel capacity.
The mechanism for these command signals would best be powerline ethernet, unless there’s a smart grid control protocol which can be used. The point is to implement data communication over the physical wires connecting the charging station with the service panel. It wouldn’t be safe to use WiFi or other wireless protocol because the charging stations might be behind multiple concrete walls (signal propagation) or attackers could crack the system over WiFi. Communications coming over that physical connection are more secure.
Lastly is the question of user authentication. So far everything we’ve discussed can be handled within the confines of the local charging network controller. It can be configured with service panel capacity and even the topology if there are multiple service panels. But what about authenticating charging station users?
With the incumbent charging networks (Blink, ChargePoint, GreenLots, etc) there is a centralized authentication system reached over the Internet. But we’re trying to avoid using such a centralized system, and keep control at the local level.
Instead of an RFID card with a card reader that might break down – what about a PIN code entered over a Bluetooth connection?
The local charging network controller could have an iPad app that a network administrator uses to configure the system. One task would be assigning PIN codes, and ensuring employees knew how to authenticate using the PIN code. Another would be designing the overall access policy – such as turning off access control in the evening or weekends to allow the public to use the charging stations.
Having the charging rate fall so low (10 amps?) is suboptimal, but it’s better than a 0 amp charging rate. Currently I hear some workplaces see real competition erupting between coworkers over access to a limited number of charging stations. Easing charging station access is therefore crucial.
The system as described might not qualify under current electrical code. I’ve been told that each charging station must be on a dedicated circuit, and the required service panel capacity is a simple calculation – the number of circuits multiplied by the rating on each circuit. (10 circuits, 40 amps each, 400 amps total)
For the system described here to work, there must be multiple levels of protection. For example the charging network controller must monitor lines, and keep the system within parameters even if one or more charging stations starts misbehaving. The measure of last resort is to completely shut off power to charging stations that don’t respond to control commands, and to completely shut down the system in extreme cases.
We going to have lots of electric cars on the road soon enough. That’s exciting, but how will there be enough charging stations?
- Apple using Tesla Megapack energy storage at California Flats solar farm - April 1, 2021
- Tesla Supercharger network finally expanding into Romania - March 31, 2021
- Volkswagen USA LIED about changing its name to Voltswagen - March 31, 2021
- Apple moving 110 suppliers to renewable energy solutions - March 31, 2021
- BMW makes deal for lithium sourced from salt lakes in Argentina - March 30, 2021
- Kia introduces EV6, with 500 km range, ultra-fast 800v charging - March 30, 2021
- Volkswagen renames itself Voltswagen to demonstrate EV embrace - March 30, 2021
- Big Lie: Wind turbines cause Texas to freeze during massive winter storm - February 17, 2021
- Shell announces shift to renewable energy, peak oil production in 2019 - February 16, 2021
- Electric Last Mile Solutions seeks to electrify delivery van market - February 12, 2021